- Location: Cardiff
- Client: Paramount D&B
- Duration: 18 weeks
- Cost: Undisclosed
- Sector: Commercial
S&G were employed by Paramount to provide a validation survey, installation and commissioning of the air conditioning and ventilation to the existing 6th Floor office area.
To ensure the new office space had sufficient air conditioning installed to satisfy the calculated peak heat loads, we modified the existing 4 pipe CHW/HTG system. This included relocating the existing fan coils to suit the new CAT B design.
We modified the existing primary and secondary ductwork to suit the new locations of fan coil units, including thermal insulation.
New condensate drainage was installed throughout serving the existing fan coils.
We installed new control valves on the HTG/CHW pipework and the supply/extract ductwork, c/w modifications to the existing control panel to suit the new control specification.
A new 10kw Mitsubishi split system was installed in the new comms room to provide 7.5kw sensible cooling to cover the peak heat load provided.
We installed a new independent shunt extract ventilation system to serve the new kitchen/breakout area.
Our scope of works included the following:
- Decommissioning of existing systems
- Reconfigure of existing CAT B Layout
- Installation of new systems to suit CAT B design
- Testing and Commissioning
- Client Demonstration
- Provision of O&M Manual